A.1 Honeywell tube based cabinet suppression system (electrical cabinet system)
Honeywell ECS system uses the detection & suppression tubing system which is installed throughout the enclosure and connected to the cylinder valve. The tubing is charged with dry nitrogen to pressurize it inside the cylinder The system uses heat-sensitive pneumatic polymer tubing that reliably detects and releases the extinguishing agent through Heat Detection Tube. Multiple temperature rated tubing options (110 or 180 degree celsius) protect a variety of hazards and equipments. Optional dual-outlet valves allow more versatility to protect larger hazards than a single valve system.
The cylinder assembly is filled with FK-5-1-12 and pre-pressurized to 195/240psi (13.5/16 Bar).
A.2 Honeywell Clean Agent Fire suppression system
Honeywell HFC -227ea
2. Honeywell UL Listed 42 Bar FK 1230 ( FK-5-1-12) Clean Agent System
General Information FK 1230 (FK-5-1-12) Clean agent system are employed to protect critical installations formerly protected by Halon 1301. FK 1230 (FK-5-1-12) agent compiles with NFPA Standard 2001 : standard for Clean Agent fire Extinguishing systems, EPA SNAP Program (Significant New Alternate Policy) These agents are classified as suitable for use in occupied areas and are considered to have no ozone depleting potential (ODP) FK 1230 (FK-5-1-12) fire suppressant can be safely used where people are present.
- Data Processing Center
- Telephone Switches
- Process Control Rooms
- Art and Historical Collections
- Archive & Museums
- Marine, Oil & Gas
- Aerospace, Aviation & Military